Three phase 400V class series (EMC Filter Built-in Type)
|*1||When selecting the inverter rating for Fuji 4-pole standard motor, consider not only the rating capacity(kW) is enough
but also inverter output current is larger than selected the motor's nominal current.
|*2||Rated capacity is calculated by assuming the output rated voltage as 440 V.|
|*3||Output voltage cannot exceed the power supply voltage.
Type 0002 to 0011：8kHz, type 0018 to 0045：10kHz, type 0060 to 0150：6kHz, type 0176 to 0520：4kHz
|*4||When the carrier frequency (F26) is set to below value or higher, the inverter is sure to be necessary to derate
its nominal current.
|*5||The value is calculated assuming that the inverter is connected with a power supply with the capacity of 500 kVA
(or 10 times the inverter capacity if the inverter capacity exceeds 50 kVA) and %X is 5%.
Be sure to use the DCR when applicable motor capacity is 75kW or above.
|*6||Obtained when a DC reactor (DCR) is used.|
|*7||Average braking torque for the motor running alone. (It varies with the efficiency of the motor.)|
|*8||Voltage unbalance (%) =(Max. voltage (V) - Min. voltage (V))/Three -phase average voltage (V) × 67 (IEC 61800 - 3)
If this value is 2 to 3%, use an optional AC reactor (ACR).
|*9||Type 0006 and 0011: allowable ambient temperature 40℃ (+104 °F) or less.
The rated output current is decreased 1% for every 1 ℃ (1.8 °F) when ambient temperature is +40℃ (+104 °F) or more.
|*10||The 400 V class series with type 0176 or above is equipped with a set of switching connectors (male) which should be configured according to the power source voltage and frequency.|